Cal-Royal 9860V / F9860V vertical rod Push Bar Exit Panic Device
Door Thickness: 1-3/4" thick standard, optional 2-1/4" thick.
Stile: 3-3/4" minimum stile width required for single door application. 3-1/2" minimum stile width required for double door application. Lever, thumbpiece and escutcheon trims available.
Chassis - Nonferrous ally (Panic Grade), steel (Fire Grade)
Cover - Brass, bronze or stainless steel. Covers stock hollow metal doors with 161 cutout.
Mounting - Furnished with wood and machine screws. Thru bolts are standard packaging on fire rated devices. Thru bolts are included and standard packaging on fire rated devices.
End Cap - Brass, Bronze or Stainless Steel Construction.
Hand - Easily field reversible.
Latch Bolt - Stainless steel.
Spring - Stainless steel.
ANSI Standard - A156.3, Grade 1.
Rail Assembly - Heavy gauge brass, bronze or stainless steel.
Dogging Feature - Allen-type key furnished standard on non-fire labeled devices. Cylinder dogging available.
UL and ULC Listed - 9860 Series for panic. F9860 Series for fire exit hardware for all types of 8' x 8' double doors for up to 3 hour fire labeled installations, conforms to standards UL10C and UBC 7-2-1997 codes.
Model: Cal Royal, Cal-Royal, 9860V3684, F9860V3684, 9880V4896, F9880V4896, 9890V3696, F9890V3696, 9850V36120, 9840V48120, US32D, US3, US4, US10, US10B
All exit devices must be listed under "Panic Hardware" in the Accident Equipment List of Underwriters' Laboratories, Inc. Where labeled doors are used as exits, they must be equipped with labeled Fire Exit Hardware and UL10C, UBC 7-2-1997 codes
All springs shall be of stainless steel throughout
All exit devices shall be of chassis mounted unit construction
All exit devices shall be ANSI A156.3, Grade 1
All exit devices shall be of touch bar design with smooth operation and be operative over 2/3 of the door's clear opening width